What should I do if the rubber gasket of the plate heat exchanger is aging?_
What should I do if the rubber gasket of the plate heat exchanger is aging?
896 Nowadays, plate heat exchangers are used more and more. However, due to the irregular maintenance and use, many plate heat exchanger gaskets often experience aging, so what should I do if the rubber gaskets of plate heat exchangers are aging? What? Next, the plate heat exchanger repair manufacturer Diguang Heat Transfer will briefly introduce the aging of the plate heat exchanger gasket. The main reason for the aging of the rubber gasket of the plate heat exchanger is usually related to pressure and temperature. In order to solve the leakage failure caused by the aging of the rubber gasket, we need to adjust the sealing performance of the plate heat exchanger and re-tighten the plate heat. Exchanger bolts, adjust the pressure of the rubber gasket between each heat exchanger to solve the problem of leakage. The maximum and minimum allowable stresses are usually given on the nameplate of the plate heat exchanger. For the plate heat exchanger just bought, the minimum allowable stress should be used to fix the connection. According to the number of plates of each heat exchanger device, the tightening force of the plate heat exchanger can be adjusted one or more times by tightening the nut 3 mm and always adjusting the plate stress during the tightening process. For plate heat exchangers that do not specify the stress adjustment range on the nameplate, the stress value is usually given in the parts drawing. For plate heat exchangers used to produce important equipment and corrosive media, it is recommended to use spare gaskets. The above is the treatment method for the aging phenomenon of the rubber gasket of the plate heat exchanger. If you want to know more about plate heat exchanger gasket materials, brands, prices, etc., please go to the official website of Diguang Heat Transfer for detailed information and consultation.